Catalog ID: MOC-9
A raised dome cover permits additional wiring room. Furnished with captive ss screws and gasket. Volume is 965 cu. in.
|Application||Mogul fittings are for use with rigid and IMC raceways. Use where standard conduit bodies do not provide adequate access and wiring area for the pulling of large and heavy conductors. For right angle bends where splices, pulls, and taps are needed in a we|
|Finish Type||Powder Epoxy Paint|
|Material||Aluminum, Copper Free (less than 4/10 of 1%)|
|Type||Mogul Conduit Body With Cover & Gasket|
|Dimensions||36 in x 6 in x 8 in|
|Gross Weight with Packaging||32.6|
Certifications and Compliance
|Hazardous Rating(s)||Suitable for use in hazardous location applications when installed according to NEC Articles 501.10(b) (Class I, Division 2) or 502.10, 503.10, and 505.15 (Class I Zone 2).|
Resources and Downloads
Please wait, preparing to download your file.