The 321 cable gland provides a seal on the outer cable sheath and is intended for use on non-armoured elastomer and plastic insulated cables. The cable gland is Exe and is suitable for installation in Zone 1 (21) and Zone 2 (22) hazardous areas.
- Provides a cable retention seal onto the cables outer sheath.
- When used in Increased Safety applications, this cable gland may be used with braided cable where the braid and the outer sheath pass into the enclosure.
- The braid must then be suitably terminated inside the enclosure.
- Note: Braided cable is classed as unarmoured cable in the EN/IEC 60079 series standards for Exe applications.
Ordering Format [ Gland Type / Size / Male Thread / Female Thread / Material / Options]; Example: 321/ C/ M32/ Brass; Example with alternative seal option: 321 / C / 1 1¼" NPT /Brass / S
|Application||Suitable for use in Zone 1, Zone 2, Zone 21, Zone 22.|
|Material||Brass (standard); Nickel Plated Brass; 316 Stainless Steel or Aluminium; Brass NPT entries are nickel plated as standard|
|Operating Temperature Range Celcius||-60°C to +100°C|
|Series||Increased Safety Cable Glands|
Certifications and Compliance
|ATEX File Number||CML19ATEX3164X|
|CSA File Number||1205533|
|IECEx File Number||CML19.0042X|
Installation/Instruction Manual (IOM)
Please wait, preparing to download your file.