The Dual certified Exe/Exd 501/414 cable gland offers a female running coupler and a seal onto the cable outer sheath for use with non-armoured elastomer and plastic insulated cables installed in conduit. May also be used with braided cables under certain conditions - See technical section for installation rules and regulations
- Elastomeric Exd flameproof seal on cable inner sheath
- Female running coupler for cable gland or conduit entry. Can be used to upgrade standard non-barrier gland into a flameproof Exd barrier gland.
|Application||Suitable for use in Zone 1, Zone 2, Zone 21 and Zone 22 and in Gas Groups IIA, IIB and IIC|
|Ingress Protection||IP66, IP67 and IP68 (30 metres for 7 days) to IEC/EN 60529 and NEMA 4X|
|Material||Brass, NP Brass or Stainless Steel|
|Operating Temperature||-60°C to +100 °C|
|Series||Group II Cable Glands|
Certifications and Compliance
|ATEX File Number||CML 19ATEX1167X CML 19.0045X|
|CSA File Number||CSA1015065|
Installation/Instruction Manual (IOM)
Please wait, preparing to download your file.